Electrical Disconnects (Elvoron)
In the machine room you will need to provide two lockable fused disconnects – one 15 amp for lighting and one 30 amp for the machine's main power. The main power disconnect may require an additional auxilliary contact for the battery circuit. Check your job-specific Garaventa Lift drawings for confirmation of details.
In accordance to the electrical code, disconnect switches should be located on the lock jamb side of the machine room door.
The fused disconnect switch rating and fuse rating for the lift will be shown on the shop drawings for your project.
At least one GFCI duplex receptacle connected to a 15 amp branch circuit shall be installed in the machine room.